1)Alternator:Stamford,Leroy Somer,Marathon or OEM Stamford,other blands brushless alternators
2)CLASS H insulation
4)self-regulator by AVR
5)50hz /1500rpm or 60hz/1800rpm
8)wave distort:less then 10%
Digital Control panel
Controller Brand: Smartgen, Deepsea,ComAp
Control Panel: English interface,LED screen and touch buttons.
1- Display loading power, voltage, currenct, frequency, speed, temperature, oil pressure, running time etc.
2Warning when low or high voltage, low or high frequency, over current, over or low speed, low or over battery voltage etc.
3Over load protection, over/under frequency protection, over/under/imbalance voltage protection, and low oil shutdown
Super Soundproof/Silent Box:
1. Excellent ventilation
2. Oil tank mounted on base frame for 12 Hours working
3. Highly Corrosion Resistant construction
4. Excellent Access for Maintenance
5. Security and Safety
6. 1m<80DBA / 7m<70DBA
7)Many colours for choice
1) Standard accessories: Standard 40 radiator mounted on skid, Common steel frame, circuit breaker, damper, exhaust silencer, flexible pipe, battery and connecting wires, Standard tools kit, operation manual and document.
2) Optional accessories: Engine coolant and oil heater, alternator space heater, cooling for heat exchanger, communiwith CAT engineion interface, battery charger by main supply, daily fuel tank, ATS and paralleling system, soundproof canopy and moving trailer.
Guarantee for one year or 1000 hours whichever reach first from ex-factory date. During the guarantee period, Genor will provide the free easy-damageable spare parts of diesel engine caused by our quality of production or raw material. After expiration, Genor provides cost spare parts maintenance of gensets.
After diesel generator installed, you can put into power, before each start, at least the following items should be checked 1. Whether unit surface and around has debris 2. Keep the into and exhaust channel of the engine room is smooth 3. The cooling liquid tank is normal 4. The air filter indiwith CAT engineor directs normal 5. Lubriwith CAT engineing oil level is within normal range 6. The fuel valve is open, the supply of fuel to engine is normal 7. Battery cables are connected correctly 8. Power load device is ready, when the generator directly with the load, breaking the air switch before start.
Packing:In Plywood cases
When we finished the test of diesel generator,our transporation department then will take charge of sending the generator to the container at port of loading,with help of our excellent forwarder,we send our generators to our customers successfully without any damage